With the continuous development of the rural electric construction, static shunt capacitor
s used in rural power supply network is more and more.
How to reduce the damage of the capacitor?
Generally can take the following precautions: 1, strengthen the patrol, inspection, maintenance, shunt capacitors should be regularly check the blackout, at least 1 time every quarter, mainly check the capacitor shell, porcelain bushing, mounting bracket parts such as dust and dirt does exist, and cleaning seriously.
Inspection should pay special attention to the connection point of the connector is rigid, whether is loose;
Shell is drum belly, permeability,
If found to have the above phenomenon, capacitor run out, must be disposed of properly.
2, control the operating temperature under normal circumstances, the general requirements of parallel capacitor shell's hot spot temperature shall not be greater than 60 ℃, otherwise, must find out the reason, for processing.
3, strictly control the operation of the operating voltage parallel capacitor voltage, must be strictly controlled within the scope of the permit.
The long running voltage parallel capacitor shall not be greater than 10% of the rated voltage value, operating voltage is too high, will greatly shorten the service life of the capacitor.
With the increase of operating voltage, parallel capacitor dielectric loss will increase, temperature rise, the capacitor to speed up the capacitor insulation aging, capacitor inside insulation breakdown and premature aging, damage.
In addition, under the operation of the high voltage function, the inside of the capacitor dielectric local aging happens, the higher the voltage, the faster the aging, the shorter the life.
Parallel capacitor if long-term operating voltage higher than the 20% of the rated voltage, its service life will be normal 0.
About three times.
So, should according to the actual situation of local power grid operating voltage, choose the rated voltage value, make its long-term operating voltage is 1 is greater than the rated voltage of capacitor.
1 times the actual operating voltage is too low, of course, is also very bad, because the parallel capacitor reactive power output by the is and its running speed is directly proportional to the square of the voltage.
If the voltage is too low, will reduce the reactive power of the output capacitor, unable to complete the task of reactive power compensation, lost should be the role of parallel compensation capacitor.
So in actual operation, must try to make the operation of the parallel capacitor voltage at its rated voltage of 95% ~ 105%, the highest running voltage shall not be greater than 110% of the nominal voltage value.
4, prevent the harmonic in power grid, there are many harmonic sources exist, if in parallel capacitor set branches in harmonic is too large, if directly into parallel capacitor, tend to make more harmonic in power grid, poses a great threat to the safety of the parallel capacitor.
Adopt the method of series reactor, can effectively suppress harmonic component and flow, to ensure safe operation in the parallel capacitor has obvious effect.
Conditional place should be prior to parallel capacitor installation place of harmonic component testing, and according to the test results to determine the required installation series reactor capacity.
The setting of serial reactor capacity, can also according to the installed capacity of shunt capacitors directly determine.
General situation is for more than five times the harmonic according to 6% of the parallel capacitor capacity selection, and for more than 3 times harmonic should be selected according to the parallel capacitor capacity is 12%.
In addition, to consider only inhibit place for more than five times the harmonic amplification problems (
The reactor is 6% of the capacity of the capacitor capacity)
Three times, but also should pay attention to prevent the harmonic amplification problems, to ensure the safe operation of parallel capacitor.
5, correct selection (
Due to the switch when switch off shunt capacitors between the static and dynamic contact arc, will cause operating overvoltage generation, in addition to claim will be (
Switch capacity to choose better than parallel capacitor group of large capacity by about 35%, also must be a contact between the insulation recovery with high intensity, small arc reigniting sex, the circuit breaker arcing good performance.
To spray oil, fire, explosion and other malignant accidents, power outage inspections shall be immediately, find out the cause of the accident after processing, can replace the new capacitor to continue running.
SMILer Electornic Industrial Co., Ltd. helps high-profile clients build strategic relationships that drive company growth, investments, funding and more. There are many make-or-break details involved in the day-to-day manufacturing within our company.
SMILer Electornic Industrial Co., Ltd. would like to provide our customers with as near perfect protection, as near perfect service as is humanly possible and to do so at the lowest possible cost.'
We are making ac motor capacitor available to you at a very low price.